Today, Shandong jingzhiyuan purification Engineering Co., Ltd. will take you to know how to design the decoration of intravenous drug distribution center reasonable and energy-saving!
1. Setting of air supply volume: the existing laminar flow operating room purification air conditioning system in Qianhai basically stops according to the industrial clean room operation scale, such as "clean workshop operation scale". This kind of operation adopts the view of "whole room concentration and purification", which can obtain the average downward air flow, has strong self purification ability, and can simplify the personal purification setting, but there are two achievements: one is large power consumption, large occupation area, and arduous music control of the wind system; the other is high cost and cover use, arduous arrangement of lamps and lanterns, and arduous plugging of high-efficiency filter. In view of the above achievements, when operating in a laminar flow operating room company, it is necessary to break through the thinking of operating room operation in terms of air volume calculation and air flow layout, introduce the view of low total air volume, strengthen partial air supply, adopt vertical one-way flow, and focus on the operating bed area. This kind of method has the advantages of convenient device cover, greatly reduced investment, and low power consumption . less occupied area.
2. Setting of fresh air section: the filtration performance of fresh air should arouse enough attention of laminar flow operating room company. In the process of passing through, the company should install its own primary effect plus medium effect filter screen on the fresh air channel, so that the fresh air passes through two-stage filtration and then becomes thick and turbid with the return air. At this time, the thick fresh air and return air are close to the dust concentration of the same particle size and scale, which really plays the role of screen medium effect and high-efficiency filter It is more convenient to wash and change the primary and intermediate efficiency filters of the fresh air filter unit. Compared with the high efficiency filter, it has less investment and light cover. The application of this method has achieved the desired results.
3. Setting of exhaust filter: in the laminar flow operating room, the air outlet shall be set above the head of the patients on the operating table, defined according to the scale, and the exhaust air volume of each operating room shall not be less than 200m3 / h. Every operating room should be equipped with exhaust fan, and the primary, middle and sub high efficiency filters should be set in front of the exhaust fan, which is often neglected. Most laminar flow operating room companies, as long as most of them are equipped with primary effect filters, the consequences are the same as that the fresh air units are not equipped with filters. When the operating room is out of service, the outdoor atmosphere will indirectly clean the laminar flow operating room through the process of exhaust, It makes the indoor temperature and humidity change quickly, the dust particles grow, and even the self-cleaning time before the next application in the operating room is extended, the filter screen life is extended, and the power is wasted.
4. Setting of air return port: the setting of air return port determines the proper air flow in the laminar flow operating room. Under the allowable indoor pressure, when the laminar flow operating room company is operating, the air return port shall be equipped with primary effect or even medium effect filter screen. Otherwise, in the operation of the indoor staff and the liquidation before and after the operation, the air return can or contains more hair and textile fibers, etc Some fibers are sucked into the return air pipeline in the process. On the one hand, it is easy to make the pipeline dust and bacteria. On the other hand, the purification of the primary filter in the unit will accelerate the replacement frequency of the filter screen, so as to increase the cover use.
The above is the introduction of Shandong jingzhiyuan purification Engineering Co., Ltd. on how to design the decoration of intravenous drug distribution center reasonably and energy saving. Welcome to the official website http://www.moptuan.com