The air conditioning system of high grade operation room should be set independently. The so-called day decoration refers to the 1000 laminar flow operation room operation room above, the reason is the high grade operation room air volume in the same area, such as the operation room, operation room 100 air volume is 3.4 times one hundred thousand, 2.25 times the million level.
The frequency of other high level is far lower than the low level of operation room operation room, so whether it is an air conditioning system for a number of high-grade operation room, or an air conditioning system for a high level and a low level of operation room operation room, will make the air conditioning system for a long time in the "big car Mara" operation.
For example, an air conditioning system for 1 100 and 2 000 operation room operation room or 4 grade one hundred thousand operation room, operation room only high grade is not used, the system planning volume at the moment at least greater than the required air volume of 112% and 84%, which is now the decoration of laminar flow operation room system required air volume is only 47% and the air volume system planning 54.3%, and the volume for operation room use and not caused by change, should not use the frequency control method of conditioning, can only use the method of conditioning air valve air conditioning total change to customary system volume, but this method was not such. Therefore, no matter from the viewpoint of energy saving or from the point of view of using flexibility and flexibility, the operation room should set up an air conditioning system independently, that is, a clean air conditioning system corresponding to an operation room.
A low level of operation room, although compared with the high level of operation room air volume is small, but for an air conditioning system of the operation room room number should not be too much, because of the use of decoration project of the hospital operation room laminar flow operation room with uncertainty. The higher the level of the hospital, the operation room in order to meet the special busy situation, the more settings.
Operation room, under normal conditions with the use factor is low, so when taking an air conditioning system in the operation room room number is large, the system often is in oversupply situation, the energy consumption is high, as some hospitals reflect "built up, can not afford". I think, on the low grade operation room, an air-conditioning system, the operation room should bear more than four to five, and a system responsible for the operation room too much, but also the formation of the use of not.