Details of the design of the intensive care unit, for the details of the design we need to understand in our life, then this is helpful to us, that is, we deal with the intensive care unit, then after completion, many people will think that the work has been completed, no longer need to operate, in fact not. In this way, the next small edition of the ICU decoration will summarize the details of the design of the ICU, hoping to help you!
The basic equipment is well equipped, and the types and types of main equipment are determined, including pulsating sterilizer, automatic cleaning and disinfection machine, ultrasonic cleaning machine, drying box, magnifying glass with light source, sealing machine, purifying water machine, acidizing water machine, receiving and sending car, air gun water gun, etc. Considering the large area of the supply room, there will be shear walls in the area. In the design, the reserved holes in the pipes and circuits of the equipments should be considered, and the shear walls should not be destroyed in the construction process as far as possible.
If steam is not provided in the hospital, an evaporator is provided in the reserved position of the supply room. There are many pipelines on the ceiling, and because of the high requirement of energy saving and heat preservation, the rooms around steam sterilizers and steam generators should consider strong exhaust. If there is no pre-consideration, the space temperature is too high in summer, the staff can not work here, and it is difficult to increase strong exhaust after the ceiling space is too small. In the design of supply room upstairs, it is necessary to consider the addition and replacement of large equipment such as steam sterilizer, to keep the passage of equipment in and out, and to facilitate the disassembly of import and export.
Steam sterilizer, steam cleaner, air gun and ethylene oxide sterilizer need positive pressure air. Considering the central air supply room, room ventilation is required, 380V power supply is reserved, and a spare oil-free air compressor and gas storage tank can be placed, stainless steel or copper pipes are arranged in advance, so as to avoid dragging one compressor per equipment. The load of power supply should consider the power consumption of high-power equipment such as electric steam generator, sterilizer, cleaner and water heater. Therefore, the power supply wire should be reserved separately.
Steam sterilizers and steam cleaners do not necessarily require the same pressure on steam. Full consideration should be given to the direction of pipelines and equipped with two sets of decompression systems. In addition, the size of steam pipe diameter should be selected according to the number and power of high-pressure sterilizers and steam cleaners. If necessary, engineers from the manufacturers should design the steam pipe diameter.
Well, today's wonderful content will be introduced to you here first! The editorial board of ICU decoration regularly organizes and publishes some industry information for you. Welcome to collect our website: http://www.moptuan.com.