In a clean operating room, the infection rate of patients can be greatly reduced, so that antibiotics that can harm the patient's immune system can be used less or not. Dust-free and sterile are the characteristics of clean operating room. The following edition will explain to you the main points of quality control of laminar flow operating room decoration project!
1. Select the construction team trained specially
Clean room construction involves decoration, HVAC, electrical and medical gas specialties. Construction personnel should have a comprehensive understanding of the construction specifications, construction technology and construction quality of clean room. Otherwise, construction quality is difficult to be guaranteed.
2. Key Control Points of Clean Room Sealing
The key content of sealing control in clean room is the construction quality of enclosure structure sealing, such as uniform coating of sealant between plate and plate to achieve tight air leakage; sockets, switches, smoke detectors, lighting boxes, medical lamp belts and viewing lamps installed on wall panels, etc. in clean room need to be used. Sealant is used for sealing, and reliable and effective sealing measures must be adopted between various pipes and boxes in the instrument cabinet.
3. Quality Control of Air Supply and Return Pipeline
The sealing of the air supply and return system pipeline is to prevent the unclean air from entering the air duct and prevent the polluted air from penetrating out of the air duct, so as to meet the cleanliness of the clean room and prolong the use time of the high efficiency filter. Pipeline processing, pipeline construction and installation quality of equipment should be mainly controlled in construction. The cleaning of air duct equipment and sealing measures in pipeline processing should be emphasized. High-quality galvanized steel sheets should be used in pipeline processing to meet the requirements of smoothness, smoothness, firmness and corrosion resistance. The noise-absorbing materials filled in mufflers should be dust-free, slag-free (fiber), moisture-absorbing and pollution-free, and should not use loose materials. Fiber materials should be felted materials, and the outer covering materials can prevent fibers from penetrating.
Thank you for reading and watching. The wonderful content of this article comes from the decoration of laminar flow operating room. We will continue to show you more wonderful contents. For more details, please click: http://www.moptuan.com.