What is the construction process of pollution decoration project?
1. Confirm the engineering design drawings and technical requirements before construction, and stop communicating with various specialties to discuss the achievements that should be paid attention to in the interpolation operation.
In engineering construction, the socket switch and viewing window are stacked due to the lack of timely communication with the electrical profession.
2. Reflect on whether the secondary information and equipment used in the project are qualified or not, and invite the owner to participate in the reflection when necessary.
Since the inspection window is not a reflection task, the inspection window is installed. The owner is not satisfied with the quality of the inspection window after the inspection, which leads to the replacement of the inspection window and the re-installation.
3. Enhance progress control and quality control in the construction process.
4. The clean room construction management system should be strictly enforced.
Fifth, in the construction of Century Star Project, the information is first to the roof, then to the wall. However, the construction starts from the vertical wallboard and then follows the ceiling. Therefore, the contradiction between the demand for construction materials and the supply of construction materials has arisen.
On the sixth, second and third floors, many slabs are erected at the bottom of the floor girder. Because of the transportation and the overhanging of pipelines, the slabs are cut and used. The ceiling height can be ordered and then sealed with iron sheet between rooms.
7. The thickness of DC flat cement and PVC floor is not considered when the door is reserved, which causes friction between the bottom of the back door and the floor of the clean room steel door device.
8. The current wind speed of the air shower chamber device is small, which can not meet the requirements of the air shower. After many introspections, it is the wrong phase sequence of the motor that causes the fan to reverse and the wind speed is too small.
Ninth, the first floor of the first floor of the board first arrival is based on the size of some drawings of non-standard boards and specifications, the rest of a large part of the construction process is to measure the size of processing. Because of the difference between the dimension of non-standard plate and the site and the lack of connection of non-standard plate, the alignment of plate joints and the short information in the process of plate layout are caused, which eventually leads to the construction halt.
To sum up, Shandong Jingzhiyuan Purification Engineering Co., Ltd. provides more knowledge of operating room decoration. Welcome to our website: http://www.moptuan.com. Thank you for your support!